I saw your website and very interesting to your product and planning to installed in different site of abra and kalinga Philippines
Also if there is demand I will help communities in the Philippines..
Can you give me a catalogue of your micro hydro sets with load controller
It has,built in load controller ?
And here in the Philippines we use 60 hz.
May I know the details of the load controller you make.
I know how to measure head and water flow using abney level and float method. So I know there is a lot of potential here especially in Northern Luzon.
We make micro hydro turbine system most efficient.
If I have the water flow and head data you can provide me a match hydro turbine you design?
The price you send to me it includes the load controller? Yes.
Great..may i know what type of load controller you offer?
Is it dummy load type?
Yes, Dump load controller.
Ah okay right..good to hear..
Can you quote me this:
Head: 90 meters
Water flow: 0.250 m3/s
We prefer pelton micro hydro turbine system
And we prefer synchronous brushless generator with AVR and synchronizer to connect in the grid
The generator is 400V/60 hz 3 phase with synchronizer To the grid
|Quotation for Micro Hydro Turbine System
|Diameter of pen-stock||300mm|
|Model||SFW160-6/590||Conforms to the IEC international electrician committee standard
|Rated speed||1000 r/min|
|Ambient Temperature||－25℃ ~ ＋50℃|
|Safety Protection||Short circuit protection|
|Over load protection|
|Over voltage protection|
|Packing Material||Fiberboard box|
|Generating Unit||Gross||Kg||2.3 T|
|Switchboard grid tie||Gross||Kg||150|
For more information, please check: www.micro-hydro-power.com